GATD42 thermodynamic steam trap.
Pressure Rating: 1.6- 6.4Mpa.
Material: cast steel.
Standard screwed: NPT.
1.Assembled with steam or air heat preservation mechanism and unaffected by the environmental humidity;with operation frequency decreased, its service life p rolonged.
2.Provided with filter screen and drainage valve .
3.The valve runs flexibly and reliably with large displacement.
By taking advantage of thermodynamics characteristics,secondary evaporation will arise when the condensate water is discharged to the lower pressure zone and meanwhile when the viscosity and density of steam differ,the drain valve will open of close.
The valve is applicable in the steam pipeline and equipment to avoid steam leakage and eliminate steam leakage in order to conserve energy and keep from water hammer and other faults.
Main technical parameters and indexes of performance.
|Maximum design pressure(PMA)||63bar g|
|Maximum design temperature(TMA)||400|
|Minimum design temperature(TMI)||-10|
|Maximum upstream pressure for saturated steam service(PMO)||42bar g|
|Maximum operating temperature(TMO)||400|
|Minimum operating temperature(TMIO)||0|
|Minimum differential pressure( PMiX )||0.25bar|
|Maximum cold hydraulic test pressure||95bar g|
Material Of Main Component.
|Name of component||Material of component|
|Valve body, valve cover||WCB|
|Minimum Order||1 Unit/Units|
|Price for Minimum Order||1 USD|
|FOB price||1.00 USD Unit/Units|
|Price for Sample|
|Sample Shipping Cost|
|Sample Delivery Time|
|Payment & Price Terms||T/T|
|Delivery Lead Time||15days|
Mr. Ellison Yue
Spriax Sarco DP17 Pilot Operated Steam Pressure Reducing Valve|